Water Leak Detection Control Panel 128 Zone
One or multiple Andel Floodline sensors can be connected to the control panel. The Floodline 128 Multi-Zone has a control unit that provides clear alarm and status updates and a base unit aiding connection of the sensor network as standard. Output relays are provided for connection to remote alarm and BMS. LEDs provide clear and easy to understand status and alarm information.
Contact T&D to discuss how leak detection control panels, sensors and cables can secure BREEAM credits for sustainable building ratings.
Function: Water leak detection, Oil leak detection, Liquid detection (volatile liquids) please contact T&D for further information), Temperature, Humidity and Refrigerant Gas detection
Zones: Multi-Zone Water Leak Detection (Capacity 32, 64, 96, 128)
Power Supply: 110/230 VAC 50/60Hz mains operated 160 Watts(max), 12 VDC internal and battery backup
Control Panel Dimensions: Base Unit: H555 x W490 x D160mm, Control Unit: H185 x W55 x D62mm
LEAK – continuous water/liquid detection – each zone reports separately
SHORT/OPEN CIRCUIT – sensor or leader cable damage, failure or disconnection
Display (control unit) Disconnected – connection cable between control unit and base unit damaged or disconnected
Display (control unit) Communication Failure – control unit and base unit damaged or disconnected
Module Communication Failure – Internal communication between base unit motherboard and 32 zone module/comms module failure
Remote Disconnected – connection cable between base unit and optional Floodline Remote Alarm damaged or disconnected
Alarm Indicators: Base Unit: Display (control unit) Disconnected, Display (control unit) Comms Failed, Control Unit: Flashing LED for alarm active plus 20×4 LCD for text description of alarms
1. Leak in any zone – SPCO Relay (5A @ 230VAC)
2. System Fault – open, short circuit any zone – SPCO Relay (5A @ 230VAC)
3. Mains Fail – SPCO Relay (5A @ 230VAC)
4. Complete Power Failure – SPCO Relay (5A @ 230VAC)
5. Self Test – Low battery, comms failure, remote/display disconnected – SPCO Relay (5A @ 230VAC)
6. Leak in each individual zone – SPCO Relay
BREEAM LEAK DETECTION SYSTEMS
Read our Blog to understand how the specification and installation of BREEAM Wat 03 Leak Detection Systems can help achieve BREEAM credits.
➡ Complete details about the full range of Andel Leak Detection cables, sensors and control panels can be found in the product sections below.